What is a current transformer 1
Worth knowing - current transformers
Plug-in current transformers, tubular bar current transformers, winding current transformers
Current transformers are special transformers for the proportional conversion of large currents to directly measurable values. A current transformer achieves galvanic separation between the primary circuit and the measuring circuit and, in the event of a fault, provides a protective effect for the downstream measuring devices. Current transformers are mainly used where currents cannot be measured directly
A current transformer converts a high primary current into an electrical signal that is easy to process. Such a current transformer emits a secondary current of milliamps up to a few amps (usually 1A or 5A) as an output signal. The secondary flow is essentiallyproportionalto the primary current.
There are different versions of current transformers for all voltage levels for use in the power grid. These have different characteristics depending on the application:
- For measuring purposes, to generate a current that is reduced proportionally as possible within the measuring range for energy meters, current measuring devices and universal measuring devices. Such converters protect themselves and the connected measuring devices in the event of overcurrent by going into saturation.
- for protection purposes, for the transmission of a reduced current to protection relays, control and regulating devices. Such converters deliver an output signal that is dependent on the primary current even in the event of high overcurrents.
Installation / connection - Connect the current transformer correctly
The connections of the primary winding are marked with the capital letters "K" and "L" or "P1" and "P2". The polarity has to be done in such a way that the "energy flow" flows from K to L or from P1 to P2. The connections of the secondary winding are with the lower case letters "k" and "l" or "s1" and "s2". The polarity has to be done in such a way that the "energy flow direction" runs from K to L.
If the connections S1 and S2 are interchanged, this leads to incorrect measurement results.
The correct determination of the power of a current transformer:
When determining the power of the current transformer, the type of connected measuring devices and the length and cross-section of the power must be taken into account. The power required by the current transformer results from the power requirements of the measuring devices and the cable.
A current transformer with too low VA power, overload, cannot maintain the class accuracy and the measurement error increases.
In the example given, you have a power requirement of approx. 3.8VA. This is made up of the internal consumption of the lines, here e.g. 3VA and the internal consumption of the ammeter of 0.8VA. In order to maintain the class accuracy, the internal consumption of the measuring devices / lines should be in the range of 25 to 100% of the converter power. With the rated power of the selected current transformer, we are in this range with 5VA.
Brief overview of the power consumption of Cu power cables:
Avoid open operation of the current transformer
A current transformer operated open on the secondary side induces very high voltage values on the secondary side. This voltage level can reach values of up to a few kilovolts and thus represents a great danger for people and the system.
Therefore, the secondary circuit should under no circumstances be opened as long as current is flowing in the primary circuit. Open operation must be avoided and the converters must be short-circuited at the secondary terminals when connecting / exchanging measuring devices.
Current transformers are divided into classes according to their accuracy. Standard accuracy classes are 0.1; 0.2; 0.5; 1; 3; 5; 0.1 S; 0.2 S; 0.5 S, as well as the extensions ext150 and ext 200 in classes 0.1; 02; 0.5 and 1. The class symbol corresponds to an error curve with regard to current and angle errors.
Rated current (Ipn, Isn)
The rated current is the value of the primary and secondary current indicated on the rating plate (primary rated current, secondary rated current) for which the current transformer is rated. Standardized rated currents are (except in classes 0.2S and 0.5S) 10 - 12.5 - 15 - 20 - 25 - 30 - 40 - 50 - 60 - 75A, as well as their decimal multiples and parts thereof. Standardized secondary currents are 1 and 5A, preferably 5A.
Standardized rated currents for classes 0.2S and 0.5S are 25 - 50 - 100A and their decimal multiples as well as secondary (only) 5A.
Rated power Sn
The rated power of the current transformer is the product of the rated burden and the square of the secondary rated current and is specified in VA. Standardized values are 2.5 - 5 - 10 - 15 - 30 VA. Values over 30 VA may also be selected depending on the application. The rated power describes the capacity of a current transformer to be able to "drive" the secondary current within the error limits through a load.
Straight-through or window-type current transformers
The conductor to be measured (busbar or cable) is passed through the opening of the current transformer and forms the primary circuit of the straight-through transformer. Straight-through converters are mainly used for mounting on busbars. Straight-through transformer or plug-in current transformer is the most common type of current transformer. These have the disadvantage that the primary conductor has to be interrupted during installation. This is why these current transformers are mainly used when setting up new systems.
In the case of small currents, the plug-in current transformer can be used as a thread-through current transformer for smaller currents for reasons of cost. The primary line is passed through the current transformer several times. The nominal primary current to be measured is reduced accordingly.
Folding transformers (divisible current transformers)
If current transformers have to be retrofitted, conversion current transformers are often used. With these converters, the converter cores can be opened during installation and thus mounted around the busbars. This means that assembly is possible without interrupting the primary conductor.
Winding current transformer
Winding current transformers or winding transformers have a primary winding for smaller currents of 1 to 40 A.
While measuring transformers should go into saturation as quickly as possible above their use current range (expressed by the overcurrent factor FS) in order to avoid an increase in the secondary current in the event of a fault (e.g. short circuit) and thereby protect the connected devices, protection transformers are required to be as far outside as possible lying saturation.
Protection converters are used for system protection in connection with the corresponding switching devices. Standard accuracy classes for protection transformers are 5P and 10P. "P" stands for "Protection". The nominal overcurrent factor (in%) is placed after the protection class designation. For example, 10P5 means that with five times the nominal current, the negative secondary-side deviation from the corresponding ratio (linear) to the expected value is a maximum of 10%.
Current transformer - measuring transducer
The advantages of the 4… 20 mA current signal are recognized and appreciated more and more frequently. With this signal, a base current of 4 mA is the zero value and the 20 mA signal is the 100% value. In addition to the general advantages of the current signal, a current of less than 4 mA can be used as an error signal.
The particular advantages of the 4 ... 20 mA signal are always evident when the transmitter is a device that is based on the2-wire principle is working.
The 4 ... 20 mA signal, that tooCurrent loop is called, makes it possible to manage the power supply and the signal evaluation with only 2 wires. The measuring transducer is constructed using a special circuit technology in which the 4 mA basic current is used to supply the transducer.
With these transducers, the auxiliary power for the internal components of the device, such as the transducer amplifier in particular, is drawn from the signal current.
- How long does a CBD cartridge last
- What's new in business automation
- How much does oracle cost
- Can I open my chakras anywhere
- How does diabetes insipidus affect urine output?
- Everyone should know what skills people should have
- Is God symmetrical
- Ayurveda does not recommend vegetarian food
- How does a capacitor block currents
- Ticks live in trees or grass
- Do you often lose guitar picks
- Which branch of math is probability
- Every college is big
- Who said the word Eureka and why
- Are Volvo cars still made in Sweden?
- Why is wood called non-metal
- What would happen if Wakanda met Themiscrya
- Which company offers the cheapest internet in Chandigarh
- What is Desi Cow Ghee
- Killed Harry Hedwig
- How does mankind get knowledge
- What day was Sachin Tendulkar born?
- How can I reduce irritation after shaving
- What is real pit grill